This feature enables you to control the 2N® Indoor Touch output relay by an HTTP command sent by 2N® IP Verso automation.
Indoor Touch settings
Navigate to the web administration and check the "Insecure HTTP Access" box. You can activate it via device menu: Settings -> Software as well.
IP Verso settings
Navigate to the web administration: Services -> Automation and create a new function according to the example below.
Description of the function below:
When you press any of the IP Verso buttons, it sends the first HTTP command to login to the Indoor Touch API. After a predefined delay it sends the second HTTP command to activate the Indoor Touch relay. Finally, it sends the last HTTP command to deactivate the Indoor Touch relay.
1st URL: http://<idt_ip_address>/api/v1/login?login=Admin&password=<your_password>
2nd URL: http://<idt_ip_address>/api/v1/gpio?action=set&name=relay1&type=value&value=1
3rd URL: http://<idt_ip_address>/api/v1/gpio?action=set&name=relay1&type=value&value=0
Please define the Indoor Touch IP address <idt_ip_address> and the password <your_password> according to your settings.
Firmware & License info
- IDT Firmware v3.53 with HTTP API license
- 2N OS v2.37 with GOLD license
- Last updated on 5th of January 2023
Note: All commands used in the Automation section are thoroughly described in our Automation manual altogether with corresponding examples.
- The manual is available on our web page: Automation Manual